The construction of Langat 2 – Phase 1 works is divided into many sub packages including Package 2A Construction of Treatment Plant which has been started in 2014. It is targeted to complete the overall Phase 1 works by end 2019.
Langat 2 Scheme
Water Treatment Plant Works
Pakej 1B: Paip Air Mentah dari Terowong Projek Air Mentah Pahang-Selangor ke Loji Rawatan Air Langat 2 dan Paip Terawat dari Loji Rawatan Air langat 2 ke Kolam Air Imbangan Hulu Langat
- Raw Water Inlet Connection Chamber at the PSRWT Tunnel Outlet Portal at the end of the PSRWT Tunnel, at a location approximately 2 km from Hulu Langat town centre.
- Raw water bulk transfer pipelines from the Raw Water Inlet Connection Chamber to the Langat 2 WTP – It consists of four (4) nos. 3000 mm dia. Raw Water Gravity Mains from the Raw Water Outlet Connection Chamber to the Langat 2 WTP to convey raw water from the PSRWT Tunnel to the WTP. Two (2) nos. will be for the Phase 1 WTP and the remaining two will be for Phase 2 WTP. Each main will connect to one Stream of the WTPs.
Pakej 2A : Construction and Completion of 1130 MLD Langat 2 Water Treatment Plant
- A total water treatment flow capacity of 2260 MLD comprising two (2) equal phases of 1130 MLD each namely Phase 1 and Phase 2.
- Current construction is for Phase 1 works that will be developed in two (2) streams of 565 MLD each.
Pakej 2B : Kuarters Kakitangan di Loji Rawatan Air Langat
- Quarters for Operators of TWP
Pakej 15 : Kerja-kerja Penyambungan Di Kolam Air Imbangan Sediada Langat
Northern Corridor Treated Water Bulk Transfer Works
Pakej 6 : Paip Air Terawat Utama dari Kolam Air Ampang ke Kolam Air AU3
- 10,046m length of 1500 mm dia. treated water gravity main from the Ampang Reservoir to AU3 Reservoir;
Pakej 7 : Kolam Air Imbangan Hulu Langat Berkapasiti 92 Juta Liter
- o Hulu Langat Balancing Reservoir 1 no. x 92 Ml with 125.0m LSD top water level
Pakej 9 : Kolam Air AU3 Berkapasiti 28 Juta Liter
- AU3 Reservoir 28 Ml with 105.0 m top water level; and
- Associated 30 m length of 1500 mm dia. inlet pipe Status – Under construction
Western Corridor Treated Water Bulk Transfer Works
Pakej 4 : Kolam Air Imbangan Bukit Enggang Berkapasiti 210 Juta Liter
- Bukit Enggang Balancing Reservoir 1 no. x 210 Ml with 114.0 m top water level; and,
- Its associated 2 nos. 1900 mm dia. treated water pumping mains connecting between Treated Water Pumping Station at the Plant and Bukit Enggang Balancing Reservoir
Pakej 5 : Paip Air Terawat Utama dari Kolam Air Imbangan Bukit Enggang ke Kolam Air Langat Sedia Ada dan Air Terawat Utama dari Loji Rawatan Air Langat 2 ke Kolam Air Imbangan Hulu Langat
- 4242m length of 2000 mm dia. treated water gravity main from Bukit Enggang balancing reservoir to the Existing Langat reservoir
- 4425m length of 1750 mm dia. treated water pumping main connecting between Treated Water Pumping Station at the Plant and Hulu Langat Balancing Reservoir.
Pakej 10 : Paip Air Terawat Utama dari Kolam Air Imbangan Bukit Enggang ke Lebuhraya Sg. Besi
- 13,000 m length of 2,500 mm dia. treated water gravity main from Bukit Engang Balancing Reservoir to Sg. Besi Highway
Pakej 11 : Paip Air Terawat Utama Dari Lebuhraya Sg. Besi ke Kolam Air Sedia Ada Bukit Dengkil
- Treated water gravity main from Sg. Besi Highway up to existing Dengkil reservoir consists of the following components:
-3,350 m length of 2500 mm dia.
-4,600 m length of 2400 mm dia.
-4,850 m length of 1950 mm dia.
-800 m length of 1400 mm dia.
Pakej 12 : Kolam Air Sg. Besi Berkapasiti 22 Juta Liter
- Sg. Besi Reservoir 22 ML with 96.0 m LSD; and,
- 200m length of 800 mm dia. treated water gravity main tee-off to Sg. Besi reservoir
Pakej 13: Kolam Air Bukit Jalil Berkapasiti 22 Juta Liter
- oBukit Jalil Reservior 22 Ml with 93.5 m top water level and its associated 150 m length of 1400 mm dia inlet pipe; and
Pakej 14: Membina dan Menyiapkan Kolam Air Petaling Berkapasiti 80 Juta Liter
- Petaling Reservior 80 Ml with 92.5 m top water level and its associated 660 m length of 2400 mm dia inlet pipe